You have every reason to feel safer if your building is equipped with a sprinkler system. The Bronx Fire Sprinklers has some nice tips on this. You can relax knowing that if a fire breaks out, your system will respond quickly to keep everyone safe by limiting the blaze until the fire service comes. This, however, will only happen if you’ve been maintaining your fire sprinkler system properly. Systems that aren’t adequately maintained may fail to function as they should, which may cost you a lot of money in the long run. So let’s take a look at what goes into fire sprinkler system maintenance and then take the required steps to guarantee you’re doing all you can.
Sprinklers in Action
But first, let’s take a look at how your fire sprinklers really function. In the movies, every sprinkler on every level of the building goes off at the first sign of fire, drenching the whole area.
But that isn’t how it works in reality. Each sprinkler head is only activated when the surrounding region is heated enough to melt the fusible connection that prevents water from flowing. As a result, a fire could only activate one or two heads, which would then try to control the flames until the authorities arrived.
What is the significance of this? We’ll go into more detail later, but the important point is that each head has its own upkeep. It’s not like they’re all connected by a single activation system, and if one fails, the others will just take up the load.
The Valve of Control
The control valve must be mentioned in any discussion about fire sprinkler system maintenance. It’s an important component of any fire sprinkler system, and it’s also one of the easiest to check. In order for the water supply to flow, there is a valve in your building that must stay open. If this valve is turned off, your sprinklers will not get any water and will be rendered ineffective in the event of a fire. Regrettably, closed valves are the most common source of fire damage.
The good news is that inspecting the valve is arguably the most straightforward aspect of fire sprinkler system maintenance. Simply check once a week to make sure it’s still in the open position.
Additionally, the valve may need to be turned off to perform maintenance or repairs on your system. If this is the case, make sure the water is turned off just in the area where the work is being done, and only for as long as it is absolutely required. There’s no need to take risks that aren’t required.
As previously said, you must turn off the valve before inspecting the real sprinklers. When you’re done, attach a brightly coloured tag or ribbon on the valve as a visible reminder to yourself or anyone else passing by that the valve has to be switched back on later.
Notify the appropriate authorities that you are doing fire sprinkler system maintenance. Your alarm provider should also be informed in case you need to activate it for a drill or maintenance. Notifying your insurance company is also a good idea. This is sometimes necessary if it means staying safe by maintaining your fire sprinkler system on a regular basis.
As previously said, just check as many sprinklers as are required and let the remainder to function normally. For the duration of the examination, you’ll also want to keep any ignition sources away of the area.